Information regarding groundwater pumping
A question from Vicky: We have a pumped groundwater to surface water system which currently extracts and discharge approximately 10,000 m3 per day through a 15" pipe. As such we are looking at investing in a small micro-hydro plant to see if it would be possible to capture any of this energy which is currently being lost. I do not know if this is a feasible idea, the efficiency rate for such a plant or even if this is something you could offer. Any information or response would be gratefully received.
The amount of energy you will regain is in proportion to the head difference between what you are pumping, and from what you are generating, so if you are pumping around 30 m head, and generating from 1 m head, then you will recover approximately 1/30 of the power usage.
It is important to know the available head between the average water level in "the large chamber" and the "settlement lagoon". You wrote the "water is sent then..." does is mean this is gravity flow? no pumping from the chamber to the settlement? If it is gravity flow then you can roughly estimate the available potential with the formula: P(kW) = Q (m3/s) x h (m) x 7; meaning you multiply the flow in the pipe (... m3/s) with the available difference in level (between chamber and settlement) and then multiply it with 7 which is a figure that considers all kind of losses (pipe losses, turbine efficiency, generator efficiency etc.). More detailed inform on using hydropower in existing infrastructure you can also find in the short flyer: http://www.skat.ch/activities/prartic... and more comprehensive information you find in the the following article: www.skat.ch/activities/prarticle.2012... If you need further support, please don't hesitate to write me an e-mail (hedi dot feibel at skat dot ch)
This thread is public, all members of KnowledgePoint can read this page.